In the HVACR world, it is not impossible that the designers of a walk-in cooler/freezer to mistakenly chose the wrong FPI (fins per inch) selection for the application you are servicing. Here is a table to reference when you are looking at possible causes of an iced-up coil. With fin spacing too close, frost can easily bridge the gap and quickly reduce air flow through the evaporator.
The proper selection of fins per inch plays a role in maintaining proper humidity levels in the conditioned space as well. The bottom line is this: don’t always assume that the application engineer can’t make a mistake in the selection process. Always look at this factor when troubleshooting your HVACR evaporator problems.