The final factor in evaluating the air distribution in a space is the comfort of the occupants. In general, a person is thermally comfortable when body heat loss equals body heat production. What most people call a “draft” is simply a slight movement of air that results in a local feeling of “coolness.” It has been determined that a velocity change of 15 ft/min has about the same effect on comfort as a 1°F of temperature change. KEEP READING BELOW…..
A typical room air distribution system with local air velocities of less than 40 to 80 ft/min will satisfy 80% of occupants. Localized air temperatures should be less than 2°F below the general room temperature. The temperature near the floor should be less than 4°F below that at about shoulder height. For heating, local air velocities generally are below 40 ft/min. For cooling, local air velocities should be between 40 and 80 ft/min.