Finding New Ways to Deal With Moisture | 2012-09-17 | ACHRNEWS. The problem of unwanted moisture in HVACR systems has been an industry evil for years. How to deal with that evil is resulting in a widening range of solutions. READ ARTICLE….
Month: September 2012
Digital Manifold & Heat Pump Analyzer | SmartHVACproducts.com.
Ductless Mini Splits Require Maintenance Too — Heres What Your Technician Will Do | Jon Waynes San Antonio Home Comfort Blog.
ASHRAE NIST Refrigerants Conference | ashrae.org. Register Now!!
What are the 7 or 8 best sustainable home improvements we can make when preparing a home for sale? – Green Home Guide by USGBC.
iOS 6 Tips and Hidden Features | Gadget Lab | Wired.com.
System Delivered BTU Calculation Basics.
If the entire load of 1,000 W is turned on, the voltmeter will read about 113 V, a voltage drop of about 2 V. A No. 14 gauge wire is allowed 15 A by the electrical codes. In this case, a load of 15 A will cause a voltage drop of about 3.5 V for …
Fluke 381 Remote Display True-rms AC/DC Clamp Meter, Clamp Meter – Fluke.